Originally Posted by ini88
I tried this too because I thought other things were effecting my temp gauge. If you do this you can only run one gauge off the sending unit. I ran two wires from the sending unit to the two separate gauges and it split the negative ground so both gauges read half of the real temp. You me just want to run a new gauge and hot wire it to a direct + line to see the true temp.
I might have to do that. What are my gauge options.
Also, what if I just re-ran a new ground to the gauge. What would be a good source for that ground?
------ Follow up post added April 1st, 2010 07:47 PM ------
Does anyone know where the gauge is grounded?